Part No.: CBL71
Circuit Breaker Lockout
a) The lock body is made of standard A3 steel plate,with high temperature spray surface treatment. .
b) Slide left and right ,adjust the card head in two gears .
c) Suitable for multi-lock management.
d) Designed to lock Schneider medium and large plastic case circuit breakers in the closed state.
Hole diameter ：8mm
Isolation preparation - specify "device isolation plan"
Identify hazards associated with the equipment to be isolated
Identify the isolation points on the flow meter diagram
Determine how to shut down and decompress equipment
Isolation preparation - energy isolation sheet
Record all isolation points on the energy isolation sheet
The energy isolation sheet shall be kept at the work site together with the work permit.
Isolation preparation - general requirements (according to operating procedures)
All personnel working in isolation must know
The equipment was shut down
The proper place to isolate
Isolate all power sources of a device
Clam preparation - general requirements (according to operating procedure)
Safely empty toxic or flammable liquids and gases
Flammable liquid discharge to the same potential to zero leakage storage area to prevent electrostatic fire
At the first flange nearest to the device to be opened, isolate the processing device
In the process of emptying or relieving the pressure of the process processing equipment, the adjacent area cannot carry out the thermal work.
Tower fan case
Circulating water cooling tower fan into the operation, the original operation has ended, maintenance personnel forgot a wrench in which. Back to the fan again, the comrade of the succession saw that the circulating water cooling tower fan was not in working state, the succession log wrote that the fan had been repaired, with the conditions for operation, without confirmation, without authorization to start the fan button, the result will once again into the maintenance personnel hanging alive.
3. The safety management department clearly stipulates that power off must be listed before maintenance, so as to effectively prevent injuries caused by the sudden start of equipment during maintenance.